This brass adaptor will renew from 80% to 90% of all orifices, enabling them to use a higher B.T.U gas. Obsolete as well as modern appliance orifices can be renewed efficiently at a minimum cost. The MI100 Adaptor is the most essential item in the serviceman’s kit. Very often, the Adaptor saves the serviceman a trip back to the shop when he does not have the proper replacement. The existing cap or plug on the appliance can be quickly renewed on the job, saving time and money.
Explanation of tools and how to install the MI100 Adaptor:
First, remove the existing orifice from the appliance and insert it in the Anvil (TL074 provided), where it is secured by the thumb screw. Next, ream out the orifice, using the Reamer (TL010 provided) in conjunction with the Hand piece (TL061 provided). Always turn the reamer in one direction. This will provide the proper size hold for the adaptor.
Remove the orifice from the anvil. Insert adaptor (which is tapered to allow for insertion) into the reamed hole.
Place the orifice on the end of the anvil. Using the Driving Tool (TL063 provided) strike with hammer to fully position the adaptor. On the end of the anvil is a small counter sunk hole located off center; place head of adaptor into this hole.
With the orifice in this position, insert the Crimping Tool (TL062 provided) and strike once or twice. This will flare the adaptor and allow an uninterrupted flow of gas.
|Part Name||Part Number||Size||Piece Count|
|Master Orifice Adapter-#72||MI100-72||#72||100|
|Handle For Reamer & Broach||TL061||1|
|Crimping Tool For Large Plugs||TL062||1|
|Crimping Tool For Smaller Plugs||TL064||1|
|Large Reamer 5/32" Diameter||TL070||1|